Yeah... it's a r ain't it?!?!?Originally Posted by Rod Gervais
The only other glitches I see are the lack of solo/pfl indicator's on each channel and a meter bridge. Otherwise, that console rips! Especially when you look at the price point!
On the acoustics front... When I was talking with the probable HVAC contractor, two points came up.
1. He indicated that local NC code says there would need to be a ridge vent and soffit vents in the "attic". This seems to be a bit of a sticky point at first glance. Doesn't that present a sound leakage issue over the CR? If so, my plan is to create vent channels out of blue styrofoam up the roof line by tacking the blue to the truss faces. Then 12-16" below the ridge/ridge vent, create a "U" baffle to at least attenuate sound.
2. HVAC is completely taken care of for the tracking area w/Unit 2. The CR and server rooms are handled by Unit 1. However, we are not seeing the rest of the lounge being services by Unit 1. Is there possibly enough capacity left on this unit to handle the lounge? -or- should I just go ahead and get a 3rd heatpump and set that outside behind the building as originally planned?